Payment & Shipping Terms:
|Working Voltage:||127/120 +/-30% ,50/60HZ||Working Environment Temperature:||-15℃～+45℃|
|Altitude:||≤1000m, Above 1000m, Derating||Relative Humidity:||≤90%|
12vdc voltage regulator,
3 phase automatic voltage regulator,
adjusted digital control voltage stabilizer
GTZW-D10-1600 KVA 1 Phase Digital Control Voltage Stabilizer Specifications
1. Working Environments
Usage:indoor,vibration-free & jolt, stabilizer no serious affection from insulation gas, steam, chemical deposition, dust, dirt and other bombings and corrosive medium.
Working Voltage: 127/120 +/-30% ,50/60HZ
Working Environment Temperature:-15℃～+45℃
Relative Humidity :≤90%
Noise <9 DB1 Mt
Terminal Block for adding phases
v LCD Large-screen
Using large-screen LCD display, can shows dynamic display voltage, current, and all kinds of working condition.
v Product Characteristics
The speed of response time(regulating speed) is very fast, non-contact, anti-interference, no mechanical failure and wear of carbon brush, maintenance-free. Three-phase voltage regulating independently to ensure the balance of output voltage . Effectively protect the security of the precision equipment.
v Precision (output accuracy) Can Be Adjusted
All precision of the stabilizer is preset plus or minus 2 Volt. According to different load demand can be adjusted plus or minus 2 Volt plus or minus 2 Volt.
v Manual Voltage Regulation
According to production requirement, within the scope of the 10% rated voltage value, the stabilizer can set voltage arbitrarily for different electrical equipment.
v Automatic Bypass Function
Equipped with automatic bypass function, when the stabilizer fails,it can turn into the mains automatically, no affection for the production.
v Output High and Low Voltage Protection Function
When monitoring circuit detect the output voltage beyond the upper or lower limit, voltage stabilizer can turn into the mains automatically, no affection for the production.
v Lack of Phase/Phase Fault Protection Function
When monitoring circuit detected phase failure, voltage regulator /stabilizer will cut off the output automatically and voice-alarm.
v Delay Stabilizing Output Voltage Function
Voltage Stabilizer boot or recover from a state of protection, would not be regulated immediately. But stay on only after users determine that the mains voltage are normal to ensure that the load equipment would not be damaged.
v Automatic Output Function
System preset is automatic output. When stabilizer connect to the mains, system detect that the power grid is normal, then it would delay <3 ms, stabilizing output voltage automatically.
v Modular Design, Easy to Replace and Repair
Adopting modular design, regulating circuit and monitoring circuits independent to each other, all components are standard-normalization. Assembly, debugging, maintenance are more simple and quick.
v Strong Load/Carrying Capacity
When the short-time overload or short-circuit, the transformer would not be damaged to avoid coil burning fire. When overload 100%, stabilizer can withstand 15 Min seconds, 10 seconds for overload 500%.
|INPUT||Rated Voltage||120/127 Vac Adjustable 90.6 /145.5|
|Stabilized Voltage Range||1P2W+G 120/127Vac+/-30%(20-60% can be customised)|
|OUTPUT||Rated Voltage||110/118/120/127 Vac|
|Center Voltage||±7℅(can be adjusted)|
|Output Accuracy||110/118/120/127Vac +/- 5%|
|THD||<1% ( not produce additional waveform distortion)|
|Load regulation||+/- 1,5%|
|Overload||500% 10Sg/ 100% 15Min/ 50% 1Hous/ 30% 2Hour 10% continue|
|PROTECTION||Overvoltage||We accept the request|
|Undervoltage||We accept the request|
|Phase Loss||Yes,uninterrupted to bypass|
|Overload||Electric detection, overload 1 minute, the output would be cut off.|
|Over-current||Electronic detection and circuit breaker dual protection.|
|Short Circuit||Electronic detection and circuit breaker dual protection.|
|Bypass||Manual bypass and automatic bypass.|
|Abnormal||Over-voltage, under-voltage, over-load, fuse blowing|
|CONTROL MODE||DSP operate metering chip intelligent control technology|
Terminal block for adding phases
|WORKING MODE||With automatic voltage regulation and the bypass, two working mode.|
500% for 10 Seconds
100% for 15 minutes
50% for 1 Hour
30% for 2 Hour
|MEASUREMENT TIME FOR CORRECTION||8.33 Ms response 1.5 us ( microseconds)|
|ISOLATION TRANSFORMER||Yes 1 for Phases|
5.Main Material List
Adopt 2.0 Thick Cold-Roll Steel Sheets.Surface treatment:G139→Phosphating+PZ660 powder+powder coating / or electrostatic
|DISPLAY||1pcs||HRD||Adopt STH wide angle LCD display,reading clearly；steroscopical and direct.|
|MAIN BOARD||1pcs||HRD||Develop PCB independently,stable circuitry;The main components adopt imported brand, like ”Infineon”, “ST”,“Fairchild”, “Toshiba”,etc.|
|SING PHASE COMPENSATING TRANSFORER||1PCS||HRD||Through secondary vacuum dipping, and continuously bake for 10 hours under the high temperature of 130 ℃.Transformer insulation class F, heat resistance 155 ℃. All the withstanding voltage are 3500V/5mA/min；|
|THREE-PHASE REGULATING TRANSFORMER||1PCS||HRD|
|RELAY||1PCS||HRD||Adopt domestic first-class brand,special customized for the Digital Control Voltage Stabilizer.|
|1PCS||Ming Rong||Adopting domestic fuse, the first brand ”Ming Rong”company’s high quality products|
Industrial-grade resistance stable and durable
|HYSTERESIS BETWEEN STEPS||< 1%|
|TECHNOLOGY||ADDITION AND SUBTRACTION PHASOR|
6.Technology and Special Requirements
1.With output manual bypass switch;
2. Enclosure material: Baosteel(or Wuhan Iron and Steel Group Corp)2mm thick cold-roll steel sheets；
3.Surface Treatment:G139→Phosphating+PZ660 powder+powder coating(RAL7032);
4.Products manufacture in accordance with the law of the People's Republic of China industry standard ,Compensating AC Stabilizer Targets.
Provide the complete technical file about the equipment :
A.1pcs The whole machine quality certification.
B.1pcs Product test report
C.1pcs User Manual
8.Quality Assurance and After-sales Service
1)Equipment warranty period is 2 year from the date of delivery;
2)During the warranty period,supplier offer technical support for free; When get the notice of the failure by the Party A, Party B should implement the warranty obligations; Reponse within 8 hours and the solution should be given without 24 hours to reduce the losses of Party A. If maintenance need other spare parts, Party B assist purchasing, installation and debugging, within 48 hours solve the problem.
3)After the warranty period, the supplier provide user with timely, high-quality, favorable technical service and supply spare parts.
Contact Person: Mr. Hunter Chen